This is the Room Alert 24ER.
It is capable of monitoring 6 external leads, and a single internal temperature/humidity monitor.
Its FQD is envmon.pmtpa.wmnet. Its IP address is 10.1.3.2. It can be configured via an HTTP interface, only accessible from our internal pmtpa vlan.
It is located in Rack B1, U41.
From testing, the internal sensor reads 0.45C / 0.81F hotter than a sensor probe directly on top of the Room Alert 24ER.
|Internal||Temperature & Humidity||Back of B1, U41|
|1||Temperature & Humidity||Front of A2, U22, Right Side.|
|2||Temperature||Front of A4, U16, Right Side.|
|3||Temperature||Temporarily on top of B3|
|4||Temperature||Front of B3, U23, Right Side|
|5||Temperature||Front of C2, U10, Right side|
|6||Temperature||Front of C3, U43, Left side|